This house is facing a blackout mainly because the last electrician uses a 4mm instead of a 10mm for the wiring inside the main switch board. After some time, the wires melt and burn out the single phase elect, main switch, cut down fuse and a 32amp MCB. We have to replace them all and rewire them with a 10mm wire which is the standard size for any normal household MSB. We also assist client to replace 3 faulty plug points. Please call us if you so require an electrician in Jalan Suakasih, Bandar Tun Hussien Onn Cheras at 012-2088629.