We came to replace a lighting switch and then inspect the reason for a power trip. We found out that one of the ballast for the fluorescent is faulty and causing the power trip, we remove the wiring for the fluorescent and power is consistent again. We didn’t replace the light as client do not wish to! Do you need an electrical inspection in Mont Kiara? Do call us!!