Do you feel the Malaysia Boleh spirit when you see my client? At least I do! We came here to do an electrical inspection especially on the water heater earthing. After that we rectify an existing 15 amp switch socket outlet which the air cond man fail to do and use a plug in method for the air conditioner. We discover the 15 amp switch socket is not faulty nor the wiring but just the MCB (something in the main switch board) is not working. We didn’t hike up the price to cheat our client like many electricians in Malaysia do by lying to our client and just rectify it at the MSB. We came back to install some fluorescent lights and I guess we won’t be seeing him soon! If you are in need of an electrician in Taman Bukit Subang, Shah Alam please do not hesitate to call us!